The low water level in a steam boiler is a situation whereby the water plunges beneath the base safe are working level as recommended by the manufacturer.With the low water level, tubes are uncovered hence no longer cooled by boiler water. The temperature of metal increases rapidly, the metal’s strength is reduced, and rupture occurs as the metals strength decreases.
Major causes of low water level in boiler:
- Feedwater shortage in the feed tank
- Feed pump Failure
- Accidental isolation of the feedwater line
- Failure of the level control system
- Inadequate operation of the emergency drain valve
- Inadequate operation of low point drain
Also, read – What is Priming In Boiler?
To prevent damages of boilers from low water level, boilers should be fitted with low water cut-offs to detect the low water condition and shut down the boiler.Also, controls should be available to monitor the water level, if the water level is reached one should take appropriate action such as sounding the alarm, shutting down the burners and the feedback supply, it is also very essential to provide an external indication of the water level.
Thermodyne Boilers are leading manufactures of World class energy efficient Steam Boilers. We are expert in manufacturing of steam boilers, thermic fluid heaters, hot air Generators or hot water generators, pressure reducing stations, steam accumulators, Chimney etc . at the affordable cost. For saving fuel cost up to 30%
call us: +91-120-4110482, 4562332/+91-9891042944 /+91-9990212122 or
mail us: firstname.lastname@example.org